Please use this identifier to cite or link to this item:
|Title:||Experimental performance of a parabolic trough collector system for an industrial process heat application||Authors:||Ktistis, Panayiotis K.
Kalogirou, Soteris A.
|Major Field of Science:||Engineering and Technology||Field Category:||Environmental Engineering||Keywords:||PTC;Steam production;Solar collector;Concrete storage||Issue Date:||15-Jan-2021||Source:||Energy, 2021, vol. 215, part A, articl. no. 118177||Volume:||215||Issue:||part A||Journal:||Energy||Abstract:||Manufacturing is responsible for 60% of the fuel consumption in Cyprus and the industrial sector is the second biggest fuel consumer, mainly for steam production. Thus, the use of parabolic trough collector (PTC) systems for the production of steam or hot water can be a promising solution for the industrial sector. This study presents the first industrial PTC system in Cyprus, installed at the biggest soft drinks factory. The system consists of 288 m2 of PTC, a steam generator and concrete thermal energy storage (CTES) in order to keep the system dispatchable. To achieve that, two operation strategies are developed which are controlled automatically by the main processor of the system. The first strategy is enabled when there is a steam demand and the second when the energy can be stored directly to the CTES. Both strategies are tested, and it is shown that under Strategy 1 the PTC system can produce 940 litters of steam per day, and under Strategy 2 it can store 107.3 kWhth. In two months period tests, it is proved that it can supply the required amount of steam to the factory even when solar radiation is low, with the support from the CTES.||Description:||The authors regret to realise a typing mistake on page 3, line 9. The number of 280 kWth should be 280 kWhth. Additionally, there is a problem in Fig. 5. The correct figure and the correct legend of the figure are as shown below: [Figure presented] Fig. 5. (a) Steam generator (b) feed water tanks (c) variable speed pump (d) control valves. The authors would like to apologise for any inconvenience caused.||URI:||https://ktisis.cut.ac.cy/handle/10488/22694||ISSN:||0360-5442||DOI:||10.1016/j.energy.2020.119288||Rights:||© The Author(s). This is an open access article under the CC BY-NC-ND license.
Attribution-NonCommercial-NoDerivatives 4.0 International
|Type:||Article||Affiliation :||Cyprus University of Technology|
|Appears in Collections:||Άρθρα/Articles|
Files in This Item:
checked on Sep 21, 2021
checked on Sep 22, 2021
checked on Sep 22, 2021
This item is licensed under a Creative Commons License